Our IP power solutions - Select the appropriate category
Our Monitoring Systems - Select the appropriate category
Our Radio Time Systems - Select the appropriate category
Choose the right accessories for our solutions
Choose your IT industry
Choose your AV area
Choose your industry
Reducing energy consumption, minimize carbon footprint - the biggest challenges of Green AV technologies
No IT without safety measures
Increased safety through out-of-band
Everything you need to know about energy monitoring
This is why energy efficiency in IT is so important
What professional environmental monitoring is all about
The right capacity planning is crucial
Flexible control through remote access
Support with basic questions
Support & Downloads for our Power Distribution Units
Support & Downloads for our Monitoring Systems
Support & Downloads for our Time Systems
Find a distributor near you
Benefit from GUDE partner status
Report your project
Read our in-depth white papers
Get to know GUDE
Meet our satisfied customers
Reach your goal faster with our well-known technology partners
All news about GUDE
A residual current, commonly called a differential current, is the difference between the current in the forward conductor and the return conductor of a powered device. If a residual current occurs on a device, it usually means that there is an undesirable current path that causes the current supplied through the forward conductor to not flow through the return conductor. Causes of fault currents can be, for example, insulation faults or defective electronic components through which an unwanted current can flow. Fault currents pose a significant safety risk for devices that operate at voltages that can be life-threatening when touched. However, there are also a number of electronic components that cause a small harmless differential current due to their design. For example, many devices of protection class 1 (devices that are operated at 230V and are connected to the mains voltage in 3-wire configuration with phase (L), neutral (N) and protective earth (PE)) contain interference suppression capacitors that dissipate a small leakage current via the protective earth conductor.
In accordance with legal regulations, fault currents in many electrical installations are monitored by residual current circuit breakers (RCDs) and, if a limit value is exceeded, lead to the rapid disconnection of the corresponding power line in order to avert possible personal injury and damage to property.
By monitoring residual currents of type B/B+, in principle all possible types of occurring residual currents, e.g. in devices with power supplies that rectify the input AC voltage into a DC voltage, can be detected.
In particular, residual current monitoring is of interest to operators of data centers in the context of the legally required electrical repetition testing: When operating electrical systems with high availability, a costly and personnel-intensive shutdown of the system can thus be dispensed with under the right technical and organizational conditions.
All terms in Expert Know-how
You can find many helpful tips, FAQs and technical information about our products in our Wiki. Here you will get help if you need special information about our products, e.g. how to query our network products via HTTPS commands or what to do if you forgot the device password.